Get the complete project »
- The Complete Research Material is averagely 52 pages long and it is in Ms Word Format, it has 1-5 Chapters.
- Major Attributes are Abstract, All Chapters, Figures, Appendix, References.
- Study Level: BTech, BSc, BEng, BA, HND, ND or NCE.
- Full Access Fee: ₦7,000
This research work presents the Application of Cuckoo Search Algorithm for the simultaneous placement of distributed generation units and shunt capacitor banks in radial distribution networks. The approaches used in most literatures for determining the optimal allocation of DG units and Capacitor banks did not consider the simultaneous placement of multiple combinations of DG units and capacitor banks in order to obtain the best combination of optimal sizes and installed an appropriate location for optimal network performance. The Cuckoo Search Algorithm was applied to determine the optimal location and sizes of Micro-DG units and Shunt Capacitor Banks with an objective of minimizing the total active and reactive power loss and maximizing voltage profile improvement and voltage stability of distribution networks. The DGs units and Capacitor banks where separately and simultaneously applied on standard IEEE 33 and 69 test bus systems and on 50 bus Canteen Feeder in Zaria distribution network. The result obtained from the simultaneous allocation was validated by comparing with that obtained from the separate allocation of Distributed Generators and Capacitor Banks. For the 33 bus test system, the Cuckoo search algorithm found the optimal sizes and locations of the best simultaneous combination of the DG units and capacitor bank allocated to be 515.69 kW at bus 25, 214.01 kW at bus 32 and 572.27 kVAr at bus 30 with 63.29% and 59.38% reduction in active and reactive power loss, 6.32% Improvement in average voltage profile and 7.89% in overall VSI, as compared to 31.65% and 31.25% active and reactive power loss reduction, 5.11% improvement in average voltage profile and 6.13% in overall VSI for separate DG placements, and 53.16% and 53.13% power loss reductions, 3,95% improvement in average voltage profile and 3.85% improvement in overall VSI for separate capacitor bank placement when compared to the base case result. For the standard IEEE 69 test bus system the optimal sizes and locations of the best combinations of DG units and CBs that were simultaneously allocated were found to be 239.83 kW at bus 53, 885.58 kW at bus 50 and 1408.79 kVAr at bus 50 with 74.29% and 79.17% reduction in active and reactive power loss, 2.34% Improvement in average voltage profile and 3.79% in overall VSI as compared to 51.43% and 54.17% active and reactive power loss reduction, 2.02% improvement in average voltage profile and 2.69% in overall VSI for the separate DG placements and 28.57% and 31.25% active and reactive power loss reductions, 1.65% improvement in average voltage profile for separate capacitor banks placement when compared to base case results. Finally for the 50- bus Canteen Feeder in Zaria distribution network, the optimal sizes and locations of the best combinations of DG units and capacitor banks simultaneously allocated was 247.19 kW at bus 23, 137.82 kVAr at bus 25 and 131.78 kW at bus 25 with 17.77% and 17.76% reduction in active and reactive power loss, 0.47% improvement in average voltage profile and 0.32% improvement in overall VSI as compared to 15.70% and 15.79% active and reactive power loss reductions,0.45% improvement in average voltage profile and 0.30% improvement in overall VSI for the separate DG placements, 9.92% and 9.87% active and reactive power loss reductions, 0.38% improvement in average voltage profile and 0.28% improvement in overall VSI for separate capacitor banks placements when compared to the base case results. From results comparison, it is evident that the simultaneous placement of DGs and Capacitor banks using the cuckoo search algorithm gave a better performance to the separate placement of the DG units and capacitor banks.
1.1 Background of Study
Electrical power systems are evolving from the conventional power systems known, where
generation plants are connected to a distribution or transmission network to new trends
involving decentralized systems consisting of small generating units connected directly to a
distribution system near demand consumption. This type of generating unit is termed
Distributed Generation (DG) (Pepermanset al., 2005). Among various DG types, the
renewable energy (Micr
You either get what you want or your money back. T&C Apply
You can find more project topics easily, just search
SIMILAR ELECTRICAL ENGINEERING FINAL YEAR PROJECT RESEARCH TOPICS
1. TO HARNESS THE ABUNDANT AND FREE SOLAR ENERGY DURING THE DAY TIME AND CONVERT IT TO ELECTRICAL ENERGY THAT WILL BE USED TO POWER SOME COMPONENTS OF AN...» CHAPTER ONE 1.0 BACKGROUND OF STUDY A solar cell is an electronic device that converts the sunlight energy directly into electric energy without any f...Continue Reading »
» ABSTRACT It has become inevitable that there would be communication and due to the inherent limitation of the human voice, the public address system c...Continue Reading »
» CHAPTER ONE INTRODUCTION 1.1 Background of study Over voltage occur in a system when the system voltage rises over 110% of the nominal rated voltage. ...Continue Reading »
» ABSTRACT This report is on stability study in electrical power system. The ability of an electric power system to reestablish the initial state (or on...Continue Reading »
5. MODELLING AND OPTIMIZATION OF A HYBRID ENERGY SYSTEM FOR GSM BASE TRANSCEIVER STATION SITES IN EMERGING CITIES» CHAPTER ONE INTRODUCTION 1.1 Background to the Study The history of the Nigerian Telecommunication Industry can be divided into three phases (Okere, 2...Continue Reading »
6. DESIGN AND CONSTRUCT AN INTELLIGENT TRAFFIC LIGHT CONTROL SYSTEM USING SENSORS AND A MICROCONTROLLER» CHAPTER ONE 1.0 INTRODUCTION Traffic control systems include signs, light and other devices that communicate with specific direction, warning, or requ...Continue Reading »
» ABSTRACTUninterruptible power supplies (UPS) are used to provide power when regular utility power is unavailable. Although they are commonly used for ...Continue Reading »
8. SOLAR POWER GENERATION FOR INDIVIDUAL IN RURAL AREA CAN SOLVE THE PROBLEMS OF POWER IN THIS COUNTRY (NIGERIA).» CHAPTER ONE 1.0 INTRODUCTION 1.1 BACKGROUND OF STUDY Energy is a basic need for the development of socio economic and enhancement of people’s living...Continue Reading »
» ABSTRACT This thesis has to do with the transfer of medical records taken remotely to a doctor via GSM wireless communication link. Specifically it ma...Continue Reading »
» ABSTRACT Traffic congestion is a severe problem in many major cities across the world and it has become and nightmare for the commuters in these citie...Continue Reading »